I’ve got a LZW31 SN installed in a 2-way non-neutral config controlling an LED motion sensing security light outside. I’ve installed a bypass at the light end of things. Unfortunately it’s really not working at all.
When I turn the switch on the security light flickers like crazy for a while and then the switch appears to reboot itself (the LED bar flashes through a series of colours and the light turns off). When the light is on the LED bar flickers blue. Turning the light off is hit or miss.
I’ve made sure to configure the switch to non-neutral mode, and I’ve disabled all the ramp and dimming steps so it should just jump straight to on/off. I’ve upgraded the switch to the beta 1.44 firmware.
As far as wiring setup goes it’s pretty basic: in the switch box I have black, white, and ground. Black is line, white is load, confirmed with a meter. In the light box I have black, white, and ground, connected to black, white, and ground on the light. The bypass is connected to black and white.
Double-check line and load at the box measured against ground. Most electricians would bring the hot in on the white conductor, but it’s not incorrect to do it the other way around. Just something to check.
Which white? You want it across the two conductors to the bulb.
Just a WAG, but even though you’ve configured the dimmer as a sort-of switch, I wonder if it still is sort of a dimmer and things aren’t working correctly because you really need a switch. The motion detector is an added dimension here. Do you have a Red switch to try? That one has a relay.
Thanks for the quick reply and suggestions. The switch installed now is a Red Dimmer. I don’t have a Red on/off around, but I do have a Black on/off I guess I could put in and try instead (although it says it needs a neutral for install, which I don’t have).
I’ll triple check the line/load. I confirmed it using an electrical tester with all wires in the box disconnected from a switch and the breaker on. The only wire that showed life was the black one. This is what I have available in the switch box:
I realize you can’t see into the box with this photo but there’s nothing to see in the box. Every wire that comes into the box is visible in the photo: one white/black/ground coming into the box, and one white/black/ground on the light fixture. That’s it.
Just curious – are you using a dimmable bulb? I know you have the switch set to a ramp rate of zero, but I’ve definitely seen this with non-dimmable bulbs even with the ramp rate set to the way you have it.
Update! I got a plain bulb socket from Lowe’s and installed it.
100w incandescent bulb with the bypass (too lazy to take it out): worked perfectly
13w LED bulb with the bypass: worked perfectly
So obviously it has to do with the light. I’m happy to replace the light with something else if I know it’ll work with the switch. I just need bright LED lights for security purposes. Is there one that’s known to work in this setup?