I have a five way circuit in my kitchen that I’m looking to add Inovelli dimmers to. I have set up ‘virtual’ three way circuits using LZW31-SN / LZW31 with group 3/4 associations previously. Unfortunately, one of the switches in this five way circuit is a double switch in a single gang form factor, so I can’t simply replace it with an Inovelli dimmer.
I’ve identified that line and load are located in the same box (where I plan to install an LZW31-SN), but I’m honestly a bit unsure on how to handle rewiring the remaining boxes. The circuit looks like this, with the last box being the one that will need to remain as a dumb switch: