I’ve created a video that I’d be happy to Google Drive link it to you (PM?). Basically, following the directions within the manual do not work for my house. My garage lights are 3-way and I have it working from the Inovelli Smart Switch, but the dummy switch won’t toggle it On if the Inovelli is Off.
The same goes for my under cabinet lighting too. It just doesn’t work following the directions. Should we be following the old method and just connecting the red wire and a neutral to the dummy switch with capping the common/load in the dummy switch box?