I’ve done about all the research I can and still can’t figure out how to install the new red series dimmer in my no neutral 3 way situation with aux. Inovelli diagrams don’t apply and I haven’t seen a thread on here with the exact same set up. I am even considering converting the 3 way to single pole just for the sake of less complexity. Can anybody confirm that’s not a bad idea?
Obviously, 3 way would be preferable. I think the most accurate diagram of my wiring would be this. The only differences being I dont have grounds and my switches are in 3 and 2 gang boxes (not singles). This is what everything looks like. Line comes into light fixture. There’s 2 romex (4 wires total) in there. 1 from each romex is twisted together and the other two go to the light. Each switch has 3 wires. Unfortunately, the wiring is quite old and the colors of the insulation have worn away, but I’ve tested the continuity of the switch wires and identified the 2 travellers. I have also identified the always hot for switch “a”. Do I need to test continuity of the fixture wires? I know which is the hot.
I feel like if I could just get some advice from some people that know a lot more than me, I could successfully get this thing installed. I want to be 100% sure where each wire goes before install everything. hope I provided enough info. Fellas, I don’t have much hair left. This dimmer is killing me, ha