No matter what i do i can’t get inovelli to work with dumb 3-way switch correctly.
So wiring setup is that line comes to 31sn, two wires one is romex b,w,g and second is b1,w1,r1,g1.
so b(line) is on switch line. b1is load and neutrals are together and in switch neutral. grounds are together. red is traveler.
on the dumb switch side, I have two wires same thing as above.
so dumb switch has three terminals. common is load (b1) from inovelli, red is traveler from invelli switch on the same side of dumb switch as common terminal and load is on opposite from second wire.
ground and white are tied together.
I have two track lights, each carries 7 lights each.
On the 31sn I went and manually did config for AC power settings 12 +1 and for dumb switch 13 +1.
At the end, same thing happens, i can turn on all lights and dim them too from inovelli switch side and I can turn them off from the dumb switch side. However inovelli will not be turned off, the blue line is fully loaded.
at the point invelli is useless until I toggle dumb switch again. Now interesting thing is that track lights are setup that B and W are on closer track and B and W are from there connecting to other track.
Also, if I would in this stage turn down inovelli and load it again, I have no lights but i get with multi meter about 90 V between black and white on entry track. i can verify that dumb switch is is switching power correctly between traveler and load.
When i toggle again dumb switch everything is fine. Ether I get lights back if they were originally loaded or i can load them on the invelli side.
So I spent way to many hours on this, and I am out of any other options.