That’s fine as long as the switch doesn’t control the receptacle. There will be many things on the same circuit (breaker).
We’re going to need better pictures. Post pictures so that we can see up into the box. While it’s important to see the connections to the switches, we need to see into the box to see all of the Romex coming into the box.
Thanks, but it’s still difficult to see into the boxes. In box one, grab that red wire nut bundle and pull it out as far as you can. We need to be able to see specifically where each of the three conductors attached to that switch are going. Right now, that red wire nut is in the way. Pull everything out as far as possible. Thx.
Box 1 BLK bundle definitely should be LINE. It may not be the one marked “LINE” with the dot, but should be the whole bunch. Otherwise, I don’t see how the switches are working. I see multiple feeds (switch on the right is clearly seen) being fed from this bundle.
The Inovelli drawing should be right as the line comes in Box 1, but is immediately jumpered to Box 2 to the switch (assuming Box 2 switch has BLK wire connected to the COM screw; its under electrical tape and I can’t see it). The jumpered back to BOX 1 on RED/WHT depending on the throw. The BOX 1 COM BLK wire is to the load.